BHTWZ00 Lafayette 3606 Engine Caterpillar parts G3606B Lafayette
Alternative (cross code) number:
Buy Lafayette 3606 Engine BHTWZ00 Caterpillar genuine, new aftermarket tractor parts with delivery
Compatible equipment models: BHTWZ00:
GAS ENGINE G3606B Caterpillar
Working with electrical circuits is hazardous and exposes personnel to electrical potential. To ensure safe operation, personnel must be trained in proper operating procedures. Bodily contact with electrical potential will cause serious personal injury or death.
High voltage is present. Work on this equipment must be performed by authorized trained personnel. Personnel must be wearing Personal Protective Equipment that meets regulatory requirements to protect the body for the work that is being performed. Failure to use appropriate PPE to protect the body will result in serious personal injury or death.
To avoid electrical shock, ensure that the inverter is disconnected from all voltage sources before performing any maintenance.
The inverter should be checked regularly for any external visible damage. Clean the enclosure lid, the display, and LEDs using a soft cloth and clean water.There are several parts to cleaning the inverter:
DC disconnect (if applicable)
Heat sinkFan Guards - Clean (If Applicable)
Illustration 1 g06142531
Example of fan guard locations
(1) Fan guardsClean the inverter fan guards when required, or if the fans make any unusual noises. Check the inverter fan guards for dirt or debris buildup. Refer to the following steps if the inverter fan guards need to be cleaned:
Ensure that the fan has stopped rotating after disconnecting all voltage sources from the inverter.
Locate and remove the fan guard from the enclosure.
Clean the fan guard with a soft brush or a damp cloth.
Replace the fan guard in the proper location on the enclosure.
Repeat Step 2 to Step 4 for any additional fan guards.Note: Components will be located in a different position depending on the inverter. Refer to the Systems Operation, Testing and Adjusting, M0074783, "Photovoltaic Inverters" for further information.Ventilation Grids - Clean (If Applicable)
Do not remove the ventilation grids permanently. Place the ventilation grids back on the inverter enclosure after cleaning. This prevents dirt and debris from collecting inside the enclosure.
Illustration 2 g06142535
Example of ventilation grid locations
(2) Ventilation gridsLocate and clean the ventilation grids regularly to maintain efficient heat dissipation. Remove the grids from the inverter enclosure and use a soft brush or compressed air